Find out about our work in more detail and take a look at our case studies.
Metro Rod (Swansea) was called out to a block of flats that had toilet issues, they were all starting to back up and almost overflow. When we arrived on site we lifted the manhole to find it was blocked and full to the top. We needed to call a vacuum tanker out so we could get some of the water out so we could inspect further. After the water level had dropped low enough we used a high power pressure washing to clean a little so we could carry out a CCTV Survey to find out what the issue was. Whilst carrying out the surrey we came across a collapse which is where the problem established from in the first place. To rectify the issue we had to excavate the area and replace the pipe. We also notice there were a few cracks in the line further and pipe lined these for the customer resolving all issues.