Will use again
8th January 2017 - in Aylesbury, Banbury, Bicester, High Wycombe, Oxford
We were called out to a job at a house a few weeks ago. There was a toilet in the house that was not flushing water away, so we sent Curtis to investigate. Curtis found a blocked manhole which was the cause of the problem with the toilet. He used his mechanical cleaner to clear the blockage and then used drain dye from the toilet to ensure that it was now running freely, which it was. During his investigation he also spotted a damaged manhole which was not blocked, but he spoke to the customer about the issues that broken manholes can cause.
The customer had this to say:
“Great job by Curtis. Will use again.”